Apologies if this question is answered elsewhere. I couldn't find it specifically.
I'm planning on installing two multi-gang switch boxes, where all of the switched lighting will be on the same branch circuit. Both of the boxes will have a 3 way switch, which in combination will control one set of lights. All other switches in these boxes are single pole switches.
I'm trying to determine the best way to provide power to each of the switch boxes. Considering I need to run travelers between the two boxes, is it permissible to run a 4 conductor cable (2 travelers, 1 hot, and 1 neutral, 1 ground) between the boxes? This allows me to bring power into one box and through to the next box for additional switched wiring.
Thanks, once again, for your help in advance!