I had a combo GFCI outlet and switch that went bad in my bathroom. The outlet worked even if the light wasn’t on. I bought a new GFCI combo switch and outlet. I had several electricians come to install. No one has been able to get both to work, only the light worked, not the outlet. I had another electrician come out yesterday and he did some moving of wires and now the light does not turn off at all.
This has been an ongoing problem for the past 3 years. I was looking while he was working on it and he said there should be more wires, not only a black and white. I don’t know what else to do. I have an old house that has old wiring. Looking for some suggestions and help.
Here is a picture of the original on the right and the new combo outlet and switch, no one knows what the wires on the back are for