I have two switches in one junction box which share one incoming line wire but each control separate lights.
I hooked up the new replacement switches using the same wiring setup which was in place for the original switches. The problem is the new switches require a neutral connection while the original switches did not. The new switches are GE z wave smart home switches and apparently this type requires neutral to be connected.
Currently the white neutral wires for the one incoming line and two loads are all bundled together with a wire nut. It would seem I need to use the jumper wire which came with each switch and merge both with the existing white wire bundle then attach the other ends of each jumper to the neutral terminal on each switch. The manual does not cover this scenario so I wanted to throw it out to this community to hopefully get confirmation I’m doing this right.
Another thing to mention is that the line wire is connected to the line terminals of the two switches in an interesting way. A small section of the wire about 6 inches from the end is stripped so the copper is exposed and that exposed section is wrapped around the screw of the line terminal on one switch then the end of the same wire is connected to the line terminal of the other switch. I want to be sure that this is an acceptable setup. Also, can I still use the approach I proposed above for connecting the neutral wires along with this odd line wire hookup?
And the last question is whether I can use any copper wire to run from the white wire bundle to my switch? I seem to have misplaced the jumper wires which came with the switches
Looking forward to comments. Thanks!