Was trying to install a new light switch and the ground wire came in contact with the hot wire. There was a spark, and I believe shortly after that the hot wire is no longer hot.
Circuit breaker in the panel did not trip, and other loads on the circuit AFAIK are still working! It is just the hot wire for the light that is now dead.
Any tips on troubleshooting this?