The Fantech FR100 fan requires Neutral & Load. That's easy enough, and the multi-switch diagram shows just a black from each switch.
The TopGreener (really Enerlites) TDHOS5 requires Neutral & Load. There are separate manual switches for a light and fan and sensors for humidity and motion. The wiring diagram shows a red wire going to the light and a brown wire going to fan. It is not clear how the neutral is used.
This is new construction so I will run what is necessary. I expect hot-black and neutral with ground from breaker to switch; black and white conductors to fan and black and white conductors to light (both with grounds). Are the three neutrals pig-tailed at switch box, before the switch?
The installation diagram is not clear: neutral is shown runing off to the opposite direction with no terminus. Just saying.
At the least, I want to wire the fan correctly!
I do want to run the one fan venting two bathrooms with two switches. TopGreener recommended this switch for this use. Lights in each bathroom are independent of each other, controlled by the motion sensor or the manual switch. The fan has a manual switch and a humidity sensor in each bathroom. The joint ventilation scheme is a way to assure fresher air in this end of the house. Also, a remote fan is quieter.
My biggest gripe is the way TopGreener has diagrammed the wiring, as it seems they should be clear(er) in regards to the neutral configuration.