I tried to upload a pic but the it says the size is too large🤨 So my breaker tripped the other day when I plugged in a set of lights. I unplugged them reset the breaker and the switch/plug combo I had the lights plugged into on. The breaker tripped again (with no lights plugged in) Reset the breaker and tried the front lights on the garage (didn't trip) and the garage door works. So I decided I needed to replace the switch/plug combo. I replaced them and now the other switch for the front lights trips the breaker also but the garage door still works fine. It's a 15 amp breaker and I have made sure to unplug everything to do the breaker tests. Any ideas? might it be a bad breaker?