I have two light switches that I would like to combine to one. See image. On the left is my existing setup, on the right is what I am thinking of doing (apologies, I never learned proper electrical diagramming). Both light switches are on the same circuit breaker.
What I gather from a similar question is that I can just cap one of the incoming wires, which I assume, is either A or C? This would mean that my idea (right diagram) is incorrect?
If that were the case, would I also cap the ground and white neutral wires from the same line?
EDIT: So I have since learned after testing the wires, that only A is hot. C was a separate light switch in another room, so it needed an uninterrupted line going to it. This still makes my diagram work.