Im passing 2 circuits and a ground from LB to junction for backyard outside circuits. So two neutral, two hot, and one ground 10 awg.
The LB box screw fell into the vertical pvc conduit last minute, and I have a few feet of wire pulled out of LB. I tried getting it but cannot. I would rather not pull the wire anymore to not damage it. I was thinking of just splitting the wire at the junction box to continue my run to the breaker box.
How many splices can a junction box contain? This is a 4 inch box.