I have a total of four receptacles a ceiling fan and a light switch. My line voltage comes in from the first receptacle, then comes out at the ceiling fan, then is wire nutted to the three other receptacles and the light switch at the ceiling. I have a total of four 12/2 wires sticking out the ceiling where the fan used to be.
When I took the fan down There was one neutral wire wired to all of the hots I believe. Would the neutral come from the switch or somewhere else? The light switch controls the ceiling fan and three of the four receptacles.