We just moved into a 2001 home. All the switches and outlets are that nasty beige color, so I am replacing them all with white switches, outlets and covers. Problem in the kitchen GFCI: I wired in a new GFCI outlet the same as the old one, and it won't reset. Totally dead. I reinstalled the old one and it works fine. Any ideas please?
GFCI receptacles can go bad, and even new ones can be defective. Try another one. (And, of course, triple check that you are wiring to the LINE terminals. And confirm that the one you are replacing will successfully Test and Reset so you know you have a clean load.)