I would like to install a 60W light for my coat closet. I can gain access to a GFI outlet on the outside wall of the closet. When I went to open up the outlet I noticed quite a mess of wires. I don't have a picture so I will explain in full detail. There are 3 cables (three blacks, three whites and three grounds) connected into the GFI.
One set of wires is going in to the "LINE" the second set goes into the "LOAD". The last set is pigtailed into the "LOAD" as well.
I am not sure if I can pigtail another line into the LOAD or should I take it from the LINE side? I dont want to overload the gfi and there is no other power source I can grab from that's close.