I installed a Siemens QT (2) two pole quadbreaker into my panel board. All 4 circuits go to the same location. The inner two breakers and outer two breakers are common trip. However due to my setup I would like all 4 breakers to trip if any single circuit breaks. I know they have tie down bars but cannot find one for a quadbreaker. Not to mention I will have to cut the existing common trip bars off. Is this safe and is there a correct way to do this. People on reddit told me to use a nail stuck through them all. However I don't think nails are UL listed ;) Below is an image of the exact breaker I used. Any input?
A breaker is a combination of an overcurrent detector and a switch, with a motor mechanism which causes one to throw the other. The motor mechanism is passive; it is a spring.
Each single breaker has enough motive power to throw its own switch, and also its partner switch.
It does not necessarily have enough motive power to throw four. You could have a horrible situation where none of the breakers trip because the other 3 are preventing the first's mechanism from operating.
You should not improvise such a thing. Contact the manufacturer for advice.
Can you live with three?
They may make 3-phase breakers for your style of panel. Obviously they are designed for phase A-B-C, but they will work fine with phase A-B-A which is what would happen if you put that breaker in a 120/240 split phase panel. Don't share the neutral!
They will not be duplex/double-stuff breakers, however.