New answers tagged workshop
With #4CU you can have up to a 90A feeder breaker. Even at 105' a 90A feeder is FINE. The sum of the breakers is a completely meaningless number, you need to consider the actual load you will have at any given time. Think about it, a typical 200A panel might be filled with 400, 500, 600, or more amps worth of breakers. Better yet do a load calculation, ...
Top 50 recent answers are included