New answers tagged cooling
Disconnected duct-work, a closed shut-off louver (somewhere in the duct-work, not at the register), or its the longest and hardest-to-run stretch, therefore possibly undersized to fit in the space or a poor job done connecting it, are all likely culprits. Contract someone who has troubleshooting experience and an inspection camera. Standard duct cleaning ...
Top 50 recent answers are included