When replacing non-grounding type receptacles is a GFCI receptacle required, or can any GFCI device be used?
Under the NEC (it was 210(7)(d)(3), but appears to have moved around some), it is permissible to replace an ungrounded receptacle with a GFCI receptacle, then wire further ungrounded or non-grounded ...
What is the maximum number of extension boxes you can hang from a ceiling? This is ridiculous and I probably need one or two more to meet the new drywall ceiling. Are junction boxes permitted behind ...
Does the circuit providing a light at the electrical panel have to be ONLY for that light? I'm fairly sure there specifically has to be a light at the panel, as well as a circuit with an accessible ...
This seems like a simple question, but I cannot seem to find the answer in the 2008 NEC. There are references to "maintaining spacing" in many sections of the code such as the following: ...