My home had an ancient Zinsco sub-panel in which the breakers were grounding out and arcing to the panel. I've swapped it with a new Eaton 100 amp panel. I've re-installed all the breakers, and re-connected everything.
When I re-energize the 100 amp breaker in the Siemens main panel, my non-contact tester shows that I have power to the new panel, but none to the individual breakers. The breakers all switch normally between the on and off positions, but I have no current. The main wires are installed in the 100 amp cut-off breaker in the panel, neutral is fixed to the neutral bar and I've installed a ground bar and connected all the ground lines.
Is there something obvious I'm missing?