I'm hoping to get some help with my thermostat problem. We bought our home brand new and it came with a very basic thermostat (non programmable and runs on batteries). I want to upgrade it to a wifi programmable thermostat so I bought a honeywell one. Our home has a honeywell ventilation system that pulls fresh air from the outside and circulates it through the home. As I read the instructions to use the g wire for the c wire it seemed easy enough. I am handy enough that I finished my own basement electrical and all do I figured it can't be too hard. So I pulled the old thermostat off after labeling the wires. Put in the new wifi one and used the g wire for the c. Went to my furnace and I have wires running all over. Into the furnace from upstairs is just a 4 wire, I have no extras. All wires are connected to the furnace board except the g wire is connected to a wire that runs up to the honeywell ventilation system and then another set of wires returns back to the furnace board. I figured out which of the return wires is the g wire and attempted to move that to the c wire in the furnace board then out a jumper in between the y and g on the same board. At first I thought this made it work because I was able to setup the wifi thermostat because it was receiving power. I setup the wifi and set the temp and the ac kicked on so I figured I was good to go. About 10 minutes later though the power to the thermostat was gone and I blew the 3amp fuse in the box. I tested it again and sure enough, after 10 minutes the new fuse blew. can anyone help me understand what is going wrong and what I need to do to fix it so I can use my new thermostat? I did call the person that installed my system and he didn't seem too thrilled about answering my questions.
I think you're out of luck, since the
If you follow the
When the thermostat energizes the
From what I can tell based on the images, this is what the whole system looks like.
On a side note. The installer that left that rats nest of wiring in the furnace, should be ashamed of himself.
The picture below you would pull the green wire off of Green at both the stat and furnace and move it to C/Common, then you jumper Yellow to Green at the furnace.