Per the 2011 NEC, is it acceptable to...
- Splice a circuit (using a junction box indoors) as long as I leave it exposed, use the correct wire connectors, and have it covered?
- Use this run one side of the spliced wire to a pair of GFCI outlets at the base of my house(outside), and the other to a switch (inside) and then to a flood light (outside)?
So can I splice and can I have outdoor receptacles on same circuit as outdoor light?
Also, If anyone knows what section either of these are covered in the 2011 NEC and could tell me that would be great too!