I am replacing an OLD h/l/v with a BROAN 100HFL
I DO NOT have a 12/2 and a 12/3 coming from the 3 switches on the wall.
I DO have this, two 12/2 coming from the 3 switches AND another 12/2 that ran to a small light that came on with light in hlv
The heater has one red and one white. The light/fan has a white/blue/black
I got the heater to work connecting the black to red and white to white..... but do not have the 3rd RED wire coming from wall switches.
I know this is out of code, but CAN NOT run new wiring.
Can someone help me out here?? I know it can be done easily, just having trouble as I am just not an electrician!