I have an oil water heater (see related question) used for a hydronic forced-air furnace. There is a backflow preventer on the incoming cold water and return hot water, and a small expansion tank on a T in the cold water intake. The tank weeps a little bit through the pressure relief valve.
Is some sort of maintenance required on the expansion tank? Does it need to be emptied?